Some companies are promoting the use of fire intumescent coatings in order to achieve a Fire Group 1 or Fire Group 2 rating when using timber wall or ceiling products. This includes claims of compliance for slotted, perforated, and slatted panels. On the face of it, there doesn’t seem to be a problem with this as it is generally in accordance with AS5637.1 and C1.10 of NCC 2019.
However, note the following regarding this:
- These products have never been fire tested on perforated, slotted, or slatted panels.
- The coating must be inspected annually to ensure it has not been removed, covered over, or tampered with. (Note that most maintenance managers would not be able to ensure this. How could they when this instruction is buried in a maintenance manual somewhere, and not in a large sign on the relevant wall!).
- The coating typically takes 3 weeks to cure.
- Perforations or slots must be free of dust.
- A 230-micron paint film is required for the base coat. This would be very hard to achieve on the edges of holes and slots of MDF panels as they are so porous and this would even be hard to achieve on the edges of interior timber battens. (Note this is typically applied on site – see diagrams below showing the effect of this).
The fact that a Codemark certificate is available is cold comfort. After all, a Codemark certificate can be withdrawn at any time.
As at the writing of this article, 46 Codemark certificates have been withdrawn, over against just 183 Codemark certificates that are still valid.
Thus, while the paperwork may be accepted by a BCA consultant, you would not have the assurance that there would not be a problem if there was a fire affecting your timber wall panels interior.
How intumescent paint must be applied as per certification (in red)
How intumescent paint is applied in reality (in red)
The above listed variances between theory and what is practically achievable is why NSW has excluded coatings for use to achieve fire ratings in the BCA.
NCC 2019 Part C1.10 NSW (b): “Paint or fire-retardant coatings must not be used to achieve compliance with the required fire hazard properties.”
Unfortunately, even though the NSW government has specifically excluded intumescent paints from their version of the BCA, anyone with a fire safety engineering qualification and general fire safety engineering experience, can register under the DBPA and approve its use!
Such is the sad state of the compliance legislation in our country. Thankfully, due to the Shergold Weir Report, all states are now addressing these problems and omissions in their legislation, although these changes may take years to filter through and affect real change.
The variances between theory and what is practically achievable with intumescent paints is also why Supawood and other professional linings companies will not use or promote the use of intumescent paints to achieve fire compliance.
Supawood ensures all our fire certifications align with how our panels are actually installed on site. We give you peace of mind that one of our fire certifications represents exactly what gets installed in your project.
If you have any questions about achieving fire compliance in your project, please feel free to reach out for advice on this important topic here.
Request a Quote
Disclaimer: All the information on this website - www.supawood.com.au - is published in good faith and for general information purpose only. Supawood does not make any warranties about the completeness, reliability, and accuracy of this information. Any action you take upon the information you find on this website (Supawood), is strictly at your own risk. Supawood will not be liable for any losses and/or damages in connection with the use of our website.
From our website, you can visit other websites by following hyperlinks to such external sites. While we strive to provide only quality links to useful and ethical websites, we have no control over the content and nature of these sites. These links to other websites do not imply a recommendation for all the content found on these sites. Site owners and content may change without notice and may occur before we have the opportunity to remove a link that may have failed.
Consent: By using our website, you hereby consent to our disclaimer and agree to its terms.